The California Fire password has particular requirements as soon as it concerns placing hand-sanitizer dispensers inside or external a facility.
UC Davis Fire avoidance Services is easily accessible to assist with ensuring hand-sanitizer dispensers are mounted in a code-compliant way in rooms and corridors.Fire prevention Services does not recommend the usage of aerosol liquid dispensers.Fire prevention Services must provide placement that free-standing dispensers both inside and outside the a facility.
Hand-Sanitizer Dispenser surroundings CodesInstallation the wall-mounted hand-sanitizer dispensers
Use that hand-sanitizer dispensers containing alcohol-based hand rubs (classified as course I or II liquids), shall be in accordance with every one of the following:
The maximum volume of each dispenser shall be 68 ounces (2 L).The minimum separation between dispensers shall be 48 inches (1219 mm).
The dispensers shall no be mounted closer 보다 1 inch (25 mm) come an electric receptacle, switch, appliance, maker or other ignition source.
You are watching: Ada height for hand sanitizer dispenser
Dispensers shall be placed so that the bottom that the dispenser is not much less than 42 inches (1067 mm) and not an ext than 48 customs (1219 mm) above the perfect floor.
Dispensers shall not release their materials except when the dispenser is manually activated. Facilities shall be permitted to install and also use instantly activated "touch free" alcohol-based hand-rub dispensing devices through the following requirements:
Dispensers shall test the dispensers every time a new refill is installed
Dispensers need to operate in a manner that ensures inadvertently or malicious activations room minimized.
Any activations of the dispenser candlestick only happen when an object is inserted within 4 inch (98 mm) the the sensing device.
An object put within the activation zone and left in place will cause only one activation.
Dispensers mounted in occupancies v carpeted floors shall just be allowed in areas equipped throughout v an approved automatic sprinkler system.
See more: What Is The Function Of A Body Paragraph Is To, What Is A Body Paragraph
In enhancement to the provisions in Installation of wall-mounted hand-sanitizer dispensers above, whereby wall-mounted dispensers containing alcohol-based hand rubs are installed in corridors or rooms and also areas open to the corridor, castle shall it is in in accordance with all of the following:
Level 2 and also 3 aerosol containers shall not be allowed in corridors.The maximum volume of each course I or II liquid dispenser shall it is in 41 ounces (1.21 L) and also the maximum volume of every Level 1 aerosol dispenser shall it is in 18 ounces (0.51 kg).The best quantity allowed in a corridor within a control area shall it is in 10 gallons (37.85 L) of course I or II liquids or 1135 ounces (32.2 kg) the Level 1 aerosols, or a mix of course I or II liquids and Level 1 aerosols not to exceed, in total, the tantamount of 10 gallons (37.85 L) or 1,135 ounces (32.2 kg) such the the sum of the ratios the the liquid and aerosol quantities divided by the allowable amount of liquids and aerosols, respectively, shall no exceed one.The minimum corridor width shall it is in 72 inches (1829 mm).Projections into a corridor chandelier not task horizontally an ext than 4 inches (102 mm) into the circulation path.
QuestionsFire avoidance Services